Note: Integrated LED systems use a 120-277V supply voltage, and are not compatible with 347V. Only CF and MH systems accommodate a 347V supply.
Incandescent and metal halide systems, and those using the 17W LED PAR 38 lamp, use a medium base lamp holder (E26).
Only integrated LED sources are supplied, not lamps.
Note: G1 and G3 globes are available with 100IN, 32CF, and 15LED max.
LED systems are available with a prismatic globe only.
Globes are not available with the 17W LED PAR 38 lamps.
The compatibility of globes depends on the light source and reflector size; please visit tmslighting.com, on the “details” page of this luminaire, and use the configuration tool.
The LED source is controlled by an advanced, integral, electronic driver that delivers consistent power.
Note: Use a current-sinking dimming system (by others) for LED dimming.
Dimming is available to systems with 120-277V supply voltage only.
Compatibility of this product is not guaranteed with all control systems.
EM: Integral CF or LED (min. operating temp. 5°C/40°F)
EMR: Remote LED (dry location only; 20 ft. / 6.096 m max. distance from EM to lamp; min. operating temp. 5°C/40°F)
EMR: Remote CF (dry location only; 7 ft. / 2.134 m max. distance from EM to lamp; min. operating temp. 5C/40F)
The test switch and indicator light would be remote.
The emergency option is not available with the 17W LED PAR 38 lamp.
The emergency CF back-up is available only with a stem mount.
See specifications in “Emergency Backups for Pendant Lights”.
Note: Brushed copper: a clear coat is applied to copper, yet, patina will form over time, depending on the humidity of the environment. The stem mount would be black.
Stainless steel: brushed; the stem mount would be flat silver.
Galvanized: rough finish on steel; the stem mount would be flat silver.
Brushed copper and stainless steel reflectors are available up to 15” in diameter.
Note: The aircraft cable is included with the drop cord, and the ceiling slope adapter is included with the stem mount.
The aircraft cable or ceiling slope adapter may be required to comply with the local seismic/earthquake code.
Follow the installation instructions, and adhere to your local electrical code.