Please log in to configure this product.
Specifications are subject to change without notice.
Control Systems — Compatibility of this product is not guaranteed with all control systems. For 0-10V dimming signal wire, use a minimum 18AWG cable.
LED Circuits — LED fixtures should be installed on a dedicated circuit. If a relay switch is required, use a solid state type. A mechanical relay could induce a surge of 10-30 times above normal.
Lead Times — This product is manufactured to order. Please contact your local sales representative for the current lead time.
Specifications and availability are subject to change.
Installation should only be performed by a qualified electrical contractor, and in accordance with national and local safety, building, and electrical codes.
Note: Lamp sockets are installed for the fluorescent and metal halide lamps. LED modules do not require a lamp socket, and are wired directly to the driver.
Note: When LED is the primary source, only the LED downlight is available. With a fluorescent primary source, either the LED or metal halide downlight is available.
Note: Use a current-sinking dimming system (by others) with this option.
The dimming option is available with 120-277V supply voltage only.
The compatibility of this product is not guaranteed with all control systems.
Note: The emergency option is available to systems with 120-277V supply voltage only.
The LED emergency back-up is available only when the 15W LED (DLED) downlight option is selected.
The test switch and indicator light would be remote.
Remote LED: (20 ft. / 6.096 m max. distance from EM to LED; min. operating temp. +5C/+40F; dry location)
Remote CF: (7 ft. / 2.134 m max. distance from EM to lamp; min. operating temp. +5C/+40F; dry location)
Note: The ceiling slope adapter may be required to comply with the local seismic/earthquake code.