Please log in to configure this product.
Specifications are subject to change without notice.
Control Systems — Compatibility of this product is not guaranteed with all control systems. For 0-10V dimming signal wire, use a minimum 18AWG cable.
LED Circuits — LED fixtures should be installed on a dedicated circuit. If a relay switch is required, use a solid state type. A mechanical relay could induce a surge of 10-30 times above normal.
Lead Times — This product is manufactured to order. Please contact your local sales representative for the current lead time.
Specifications and availability are subject to change.
Installation should only be performed by a qualified electrical contractor, and in accordance with national and local safety, building, and electrical codes.
Note: Only CF and MH systems are compatible with 347V. Incandescent systems are compatible with 120V only.
Incandescent and metal halide systems, and those using the 17W LED PAR 38 lamp, use a medium base socket (E26).
The LED source is controlled by an advanced, integral, electronic driver that delivers consistent power.
Note: G1 and G3 are used with 100IN, 32CF, and 15LED max.
The LED dimming option is the 0-10V,current-sinking type.
Note: Use a current-sinking dimming system (by others) for LED dimming.
Dimming is not available with 347V or 17W LED systems, or for outdoor CF applications.
Compatibility of this product is not guaranteed with all control systems.
Note: The emergency option is not available with the 17W LED PAR 38 lamp.
See specifications in “Emergency Backups for Pendant Lights”.
Note: The aircraft cable or ceiling slope adapter may be required to comply with the local seismic/earthquake code. Follow the installation instructions, and adhere to your local electrical code.
Note: A clear coat is applied to copper, yet patina will form over a period.