Please log in to configure this product.
Specifications are subject to change without notice.
Control Systems — Compatibility of this product is not guaranteed with all control systems. For 0-10V dimming signal wire, use a minimum 18AWG cable.
LED Circuits — LED fixtures should be installed on a dedicated circuit. If a relay switch is required, use a solid state type. A mechanical relay could induce a surge of 10-30 times above normal.
Lead Times — This product is manufactured to order. Please contact your local sales representative for the current lead time.
Specifications and availability are subject to change.
Installation should only be performed by a qualified electrical contractor, and in accordance with national and local safety, building, and electrical codes.
Note: The metal halide lamp must be the E-17 bulb type with an E26 base.
Lamp sockets are supplied for CF and MH systems. LED modules are wired directly to the integral driver, and do not require a lamp socket.
Integral LED systems operate with a 120-277V supply voltage, and are not compatible with 347V.
Integrated LED sources are supplied, not lamps.
Louver: Manufactured with high grade aluminum, and available in the anodized or white finish to maintain its reflective properties.
Note: The louver is available with CF and MH systems only.
Diffuser: The cylindrical diffuser is formed with clear, UV-stabilized acrylic. It provides a slight degree of diffusion, while protecting the internal components.
Note: The test switch and indicator light would be remote.
Integral CF or LED: (min. operating temp. +5C/+40F)
Integral CF or LED with cold pack: (min. operating temp. -20C/-4F)